Site Preparation & Installation
The preparation of the pad for your Rhino Tank is the responsibility of the customer. Our preferred base material is fine crusher dust; however, if crusher dust is not available in your area please insist on using screened course river sand. It must be free of sticks, stones and clay lumps (6mm diameter or less).
Level Pad (+/‐ 10mm)
Minimum thickness of pad is 150mm or 6 Inches
Dimensions are outlined in the pad size/specification sheet below.
Ensure adequate compaction of the sub soil to avoid subsidence for deep pads.
The customer is required to place an exclusion zone of minimum 10mm Blue Metal/Stone (no clay or concrete) around the base of the tank after installation to prevent erosion and deter rodents from digging around the base.
If Site Access or the Pad Quality is not adequate, it may be necessary for our installation team to leave the tank and re‐schedule the installation (possibly weeks) until the problem is corrected. Unfortunately, this will incur additional charges over and above the specified cost (to cover wages and travel).
Site Access .
Please ensure adequate access to the site for a small truck or 4WD and trailer, bearing in mind soil and weather conditions.
Access is to be available to within 10 metres of site
If unable to meet these requirements please contact Tanclean- Rhino Water Tanks to make alternative arrangements.
On The Day
You are most welcome to attend on the day but it is not essential. It is difficult to finalise a particular installation date in advance due to the weather, freight and labour.
The Customer is required to arrange water supply of a minimum of 35 - 40 % volume of tank capacity being built in terms of literes of water upon competation to stabilize the liner. This amount represents an average of a single tanker load of water for the smallest size of ourtank: RT-25. Please note that tank installation may have to be postponed and additional charges would be levied in case water is not made available immediately after installation.
Note: Rhino Water Tanks & Liners are suitable for the storage of water within a PH range of3-7, and a Temperature range of -6 Deg Cent. to 40 Deg. Cent.
A Tax Invoice will be forwarded upon notification by the installation team of PracticalCompletion. Payment towards supply has to be made against Proforma Invoice andinstallation charges payment immediately on successful erection and commissioning. (unless otherwise arranged and approved by Tanclean management in writing).
PAD SIZES AND QUANTITIES OF SAND, GRAVEL & WATER REQUIRED
|Tank Model||Capacity in Liters||Minimum PadDia in Mts/Ft.||# Qty. of Sand/CrusherDust at 150mm /6” deep||# Qty. of Blue Metal/ Stone||Water Reqd.(Lits)|
|RT-25||26,062||5.50m / 18||Ft 4 CM / 150 CF||2 CM / 75 CF||10000|
|RT-40||40,723||6.50m / 21 Ft||6 CM / 200 CF||3 CM / 100 CF||16000|
|RT-60||58,640||7.50m / 25||Ft 8 CM / 300||CF 4 CM / 150 CF||24000|
|RT-80||79,816||8.50m / 28Ft||10 CM / 350 CF||5 CM / 175 CF||32000|
|RT-100||104,250||9.50m / 31||Ft 12 CM / 450 CF||6 CM / 225 CF||40000|
|RT-130||131,941||10.50m / 34 Ft||15 CM / 550 CF||8 CM / 275 CF||52000|
|RT-160||162,890||11.50m / 38 Ft||18 CM / 650 CF||9 CM / 325 CF||64000|
|RT-200||197,097||12.50m / 41 Ft||21 CM / 750 CF||11 CM / 375 CF||80000|
|RT-230||234,562||13.50m / 44 Ft||25 CM / 900 CF||13 CM / 450 CF||90000|
Suggested Pad Levelling Technique
With a spirit level on top of a screed, level out the sand or crusher dust using a temporary pole in the centre of the pad as a pivot point.